Heat pump Bryant Repair in San Jose, California – turned off by itself
Heat pump Bryant start working few minutes and stops. The reason why it’s doing like that was fan thermostat – the G wire had bad contact. Condenser unit started and overheats evaporator coil and for that reason pressure was too high and cutoff power to compressor. After fixing wire – everything started working perfect.