RUUD Air Conditioner UAKAß048JAZ Shutdown – Overload – in San Jose, California
RUUD Air Conditioner UAKA-048JAZ
Since parts of the electrical line didn’t match the Amper range at the condenser, the working range is 40 Amp and the breaker was set to 20 Amp and 60 Amp fuses, the breaker was turned off when the power was overloaded. The breaker is replaced with 40 Amp, the fuses with 40 Amp. Unit works.