Water Heater Rheem Performance Repair in San Jose, California – 2 flashes error Honeywell gas valve- Low voltage thermopile
The water heater did not work. Gas control valve Honeywell blinked with 2 lights and means low voltage thermopile. I did check pilot generator – it was good. I did try light pilot and it started. Then I turned valve switch and gas start flaming. And after 5-7 seconds gas valve Honeywell shutdown – with same error. I noticed that water collected on bottom dish. It was a reason. For water heater wasn’t enough oxygen for combustion. I made 3 holes on bottom dish and water coming out. After that water heater Rheem Performance start working fine. I said customer call to plumber for fix leaking pipes.